Plumbing Repair Service in Johns Island, SC
Plumb Pro® is your best choice for repair, installation, and service in homes and buildings just like yours in the Johns Island, SC area.
We take special pride in the craftsmen we train and employ–a fact you’ll see in their reviews below. It’s also noticeable immediately in the attitude and integrity our technicians bring to your job site. Our entire company works hard to make your experience with us hassle-free and enjoyable. You can also be assured that Plumb Pro® stands behind the work we do as well as comply with all local codes.
We handle all your plumbing needs including leaking pipes, hot water heater problems, and drain or sewer issues. Call us today at 843-940-PROS(7767)!
Service techs were cordial, knowledgeable and provided excellent service.
The young man you sent out was very pleasant and professional
All of a sudden I had NO water pressure at my house, literally just a trickle. After a phone call, and two unanswered emails to the original well installer, I called Plumb Pro because of their super reviews. Jim came out at 7:45 P.M.! He quickly found the problem (my old well filtration system was shot) and got my water running until the new system could be shipped and installed. He explained and showed me what had failed and thoroughly explained my options. He replaced my old system with a new filter system that includes an ultra violet light sanitizer. Also, I chose to buy the service plan offered. Plumb Pro will not only check the well system and replace the filters for me every 6 months, but will also check the rest of the plumbing. This gives me great peace of mind. Just wonderful service (and no more having to deal with an unresponsive, unprofessional well man). I am so excited about my new "state of the art" system.
We had a leak in our Water Heater and Mike arrived early that morning. He spent time with us reviewing our options, his service was professional and fast and we will call him again!
Technician was very knowledgeable and provided great, timely, efficient service
Building has a trap station for all floor drains. Test trap station. Water backed up out of floor drain in front of freezer. Cabled to clear
Smell in building.
Replaced anode rod with powered up anode
egg smell water heater Bradford White.
Anode in state water heater replacing
Rotton egg smell coming from water heater
Replaced cartridge in Moen valve flushed Rinnai tankless water heater and inspected plumbing
Shower valve won't turn off
Resealed kitchen sink and repaired outdoor shower
Auger sewer line
Toilet cable stuck in toilet.
Aquasauna well water filtration
Estimate to replace/repair kitchen faucet
Repaired sewer line
Grease trap and drain jetting
Well water filtration system. Aqusana